- Time:2019-08-21 14:36:54
- Direct supply from the factory
- Ordering hotline:
The centrifugal chiller uses electricity as the power source. The Freon refrigerant evaporates and absorbs the heat of the brine water in the evaporator for cooling. The vaporized endothermic freon vapor is compressed by the compressor into a high temperature and high pressure gas. After condensation, it becomes a liquid and is throttled into the evaporator through the expansion valve. Thus, 7 ° C - 12 ° C chilled water is prepared for air conditioning at the end of the central air conditioner.
A two-stage refrigerating compressor with a fully inclined aluminum alloy impeller.
Semi-closed motor: cooled by liquid refrigerant, constant temperature and high efficiency.
Working principle: The blade rotates at high speed, and the speed changes to generate pressure, which is a speed compressor.
Less moving parts, low failure rate and high reliability.
The coefficient of performance is high, generally above 6.1. 15%-100% load operation can achieve stepless adjustment, and the energy saving effect is more obvious.
The cooling capacity of centrifugal chillers is mainly caused by water quality: the condenser and evaporator of the unit are heat exchangers. If the heat transfer tube wall is fouled, the cooling capacity of the unit will decrease, but the condenser and evaporator are in the process of designing the manufacturer. It has been considered to be easy to clean, and its cooling capacity has a long decay with the use of time, and the cooling capacity is rarely attenuated.
A combination of a two-stage centrifugal compressor + a spray evaporator.
This design enables the machine to maintain a high energy efficiency ratio at part load and stable operation in complex environments and large load changes, greatly improving the stability and reliability of the unit.
First: the two-stage compression energy efficiency ratio is high.
The operating range is much larger than single-stage compression and it is not easy to enter the surge zone. The cooling efficiency is high, and when the load is reduced, the efficiency attenuation is extremely small. The speed of the compressor impeller is reduced and the wear of the bearing is reduced. Thereby improving the operating life of the unit. Avoid compressor surge problems under low load conditions.
Second: the spray evaporator has much better energy efficiency and maintainability than the full liquid evaporator, and the R134a charge is relatively small.
The refrigerant entering the evaporator is sprayed downward from above the heat exchange tube array. The liquid refrigerant forms a film on the tube wall and flows downward. The refrigerant circulation pump is used as the refrigerant throttling device of the economizer to the evaporator, and the liquid refrigerant at the bottom of the evaporator is extracted and recirculated to increase the supply of the refrigerant above the array in the evaporator, so that all the copper pipes can cover the liquid refrigerant. The unit does not need to accurately correct the level, only for general positioning, the evaporator can play normal and efficient functions.
The unit does not need to be overhauled, only the cleaning of the water system is required, and the maintenance cost is low.
Electric refrigeration has a history of more than 100 years, with mature technology and manufacturing processes, convenient use and maintenance, and has become a popular product for many users.
The average life of the centrifugal compressor is 80,000 hours. The unit freon and oil have been added, and the user can use the water and electricity on site.
1. The main control parameters of centrifugal chillers are refrigeration performance coefficient, rated cooling capacity, surge and energy efficiency ratio at partial load, input power and environmental protection of refrigerant type.
2. The selection of the chiller should be considered according to the cooling load and use.
3. When a chiller is selected, the unit with a higher coefficient of performance value is preferred. When the design is selected, it is generally selected according to the large amount of cold that may be required under extreme conditions. According to statistics, the average chiller operating time under 100% load is about 1/4 of the total running time. The operating time ratios of 100%, 75%, 50%, and 25% of the total operating time were approximately 2.3%, 41.5%, 46.1%, and 10.1%. Therefore, when selecting a chiller, priority should be given to models with a flatter efficiency curve. It is recommended to use a two-stage centrifugal compressor + spray evaporator solution. At the same time, the adjustment range of the chiller load should be considered when designing and selecting.
- SYFU032 cage filter
- FZ40/35 axial fan
- PWF40/45 spray axial flow fan
- BX-1 swinging return air filter
- SYZH series cone ring type dust removal unit
- SY type air washing room component
- Spray pipe
- Fan series
- Air volume adjustment window and fixed louver
- Sy type flap
- SY type variable air volume return air filter
- Sy052 dust compactor
- Water pump and pipe fittings
- Adjustment window
- Light pipe heater
- Stainless steel water filter
- Electric control cabinet
- SYFU002 waste cotton processor
- Dust collector
- FC6-48 dust exhaust fan
- Sy042 fiber separator
- Dust removal equipment
National Sales 顺心彩票 Hotline
Copyright ? 2019 顺心彩票 版权所有
小泽玛利亚 樱井步 苍井空 石黑京香 桃谷绘里香 白咲舞 川岛和津实 黑泽爱 樱井步 小泽爱丽丝 七濑茱莉亚 樱朱音 原千寻 若菜奈央 稻森丽奈 尾野真知子 友田真希 花野真衣 雪本芽衣 雨宫真贵 冲田杏梨 高阪保奈美 霞理沙 泽井芽衣 北野望 桃谷绘理香 橋本凉 波多野结衣 仁科百华 柚木提娜 长泽梓 大沢佑香 天海翼 前田香织 前田香织 二宫沙树 铃木里美 希崎杰西卡 麻仓优 麻美由真 原更沙 葵实野理 上原瑞穂 福山沙也加 铃木麻奈美 西野翔 神谷姬 希志爱野 琴乃 希崎杰西卡 秋元里奈 原干惠 杏树纱奈 佐藤遥希 Sato Haruki 前田香织 二宫沙树 仁科百华 樱木凛 秋元里奈 小泽爱丽丝 原纱央莉 浅井舞香 音羽雷恩 天海丽 大泽佑香 百合野もも 里美尤里娅 铃原爱蜜莉 美竹铃 吉沢明步 吉泽明步 早川濑里奈 美竹凉子 松岛枫 佐佐木希 樱井梨花 立花美凉 小泉彩 里美尤里娅 铃原爱蜜莉 美竹铃 松岛枫 佐佐木希 朝美穗香 上原结衣 纹舞兰